Our air conditioning unit was forever tripping the breaker switch that gave its power.
I called the Heating, Ventilation, plus A/C supplier numerous times when our air conditioning refused to work.
They kept telling me it was our breaker switch that was faulty plus not the air conditioning unit. I called an electrician, but he couldn’t find anything wrong with our electricity. He said the air conditioning unit had to have a short in its electrical system. I wired the breaker switch for 220 plus it should be able to support the entire Heating, Ventilation, plus A/C plan plus not just the A/C unit. Once again, I was back to calling the Heating, Ventilation, plus A/C supplier. I told them I needed to have a Heating, Ventilation, plus A/C serviceman come to the home plus check the electrical plan in our air conditioning unit. The operator argued with me plus told me they had previously worked on the A/C unit plus found nothing wrong. I insisted she send a Heating, Ventilation, plus A/C tech to the house, plus I would not quit calling until she agreed. I entirely threatened her task if she didn’t send someone over. I was going to call the owner of the supplier. Two hours later, I had a Heating, Ventilation, plus A/C serviceman driving up. He showed me his badge plus said he was a new serviceman with the supplier. It took about twenty hours before he found the problem. There was loose wiring in the system, plus it was tripping the breaker switch. I thanked him for finding the problem plus after that I called the Heating, Ventilation, plus A/C supplier plus thanked them for finally sending a competent serviceman to our home.